How to diagnose a System Trouble on the DACT Dialer
To diagnose why the System Trouble LED is lit on the DACT Dialer.
1.) Connect the programming keypad (FMR-DACT-KEYPAD, D7033, or DS9447) to the dialer using the 5 pin harness.
2.) Press 1 Status - This will list all the troubles on the DACT.
Trouble Keypad - the Keypad is connected to the DACT - (you should see this trouble only, all other need to be corrected)
Trouble Phone 1
Trouble Phone 2
Trouble with one of the points
Trouble Progamming - This is caused by not programmed one or more of the following prompts:
Phone #1: ?????????
Phone #2: ?????????
Phone #1 Format:
Phone #2 Format:
An Account number, phone number and format needs to be entered in each field.