This website uses absolutely necessary cookies. If you consent to the use of convenience cookies, please click “Yes, I agree.” By clicking on “Privacy Settings.” you can change this setting at any time and withdraw your given consent.
You can find detailled information in
Decide which cookies you want to allow.
You can change these settings at any time. However, this can result in some functions no longer being available. For information on deleting the cookies, please consult your browser’s help function.
On the DS9400, DS9400M, D7024, and FPD-7024 Fire Alarm Panels the Water-Flow timer can be set from 0.5 seconds (fast) up to 89 seconds. This timer feature is programed in Program Points > Point Functions. Only One Point Function timer can be set. (Example - if function 4 as a Loop Response Timer set to 16 seconds and you add a second function like function 12 with a Loop Response Timer of 60 Seconds - Both Function 4 and Function 12 will have a Loop Response Timer of 60 Seconds. Now if a third function is added like function 2 with a Loop Response Timer of 30 Seconds, now Functions 2, 4, and 12 will have a Loop Response Timer of 30 Seconds.
*Note: A limit of 20 points may be assigned to point functions that have been programmed with a response time other than 0.5 seconds (Fast).