Panel controller displays can become de-calibrated, e.g. upon initial power-up followed by unintentional contact with the display or inaccurately touching the crosshairs.
It becomes noticeable after the panel controller has re-booted and does not respond properly to touch.
To silence all NAC's of one panel (FPA-5000/Avenar) from the map in FSM
Insert a sensor on the map of FSM
Under sensor properties choose:
Add symbol: FIRE_Panel_FPA_BG
Driver Instance: the panel / compound where the FSM is belongs to
Address-> e.g. Panel 1-10.1
! Please pay attention: there are other “Panel” possibilities to choose. Please do not choose Panel 1-10 (Communication)!
After inserting the settings click “ok”
At the map when you right click the panel symbol you will get the commands as shown below.
If there is a fire alarm, you can right click at the panel and then click at “silence on”.
Please be sure, that then every NAC which is belonging to this panel is “silenced”.
Additional: there is also a command "silence scope" which then has the effect, that the whole scope will be silenced.
Follow the steps from this article to configure FPD-7024 to communicate using Cellular or Ethernet network communications.
How to configure the FPD-7024 for network communications using keypad programming.