FLM-325-2i4, FPA-1000, FPA-1000UL, FPA-1000V2
How the FLM-325-2i4 Reports to the Central Station (CS).
The FLM-325-2i4 addressing using the D5070 Hand Held Programmer.
The FLM-325-2i4 is addressed as 1 address only.
The First input will display as xxx.1 on the panel keypad display, the Second input will display as xxx.2 on the panel keypad display.
It reports to the CS as xxx for the first input and xxx for the second input.
For the CS to destinguish between xxx.1 and xxx.2 it is recommended to program each input as a different function.
Program xxx.1 as a Fire Input and program xxx.2 as a Supervisory.