In the event of flames and smoke, the camera's built-in intelligent algorithms analyze the scene in real time by concatenating and transforming the input data. Deep learning AI directly analyses the data and if a fire is confirmed, it triggers an alarm and sends a signal either to the fire panel or the Video Management System.
Thanks to the latest AI technology and deep learning methods, the newest generation of fire detection cameras AVIOTEC 8000i IR becomes the best, fastest and more robust option for applications where traditional detectors might find limitations.
Panel controller displays can become de-calibrated, e.g. upon initial power-up followed by unintentional contact with the display or inaccurately touching the crosshairs.
It becomes noticeable after the panel controller has re-booted and does not respond properly to touch.
The FLM-325-2i4 is a Single address Dual Input Analog Addressable Module with two inputs used to monitor Normally Open (NO) or Normally Closed (NC) circuits. If the module is addressed as 010 the First input will display as 010.1 on the panel keypad display, the Second input will display as 010.2 on the panel keypad display.
What does it mean when the panel displays a trouble of "Dialer Answering Unknown"?
"Dialer Answering Unknown" is caused by the panel answering an incoming phone call. This will cause a trouble tone from the panel that will clear itself when the panel releases the line, this may take up to 10 minutes. If another event (Alarm, Trouble, Supervisory) occurs during this time, the panel will drop the line and dial out to the central station.
To prevent or stop this set the Line 1 Ring Count to (0).