Question - How did all my single point modules change their Action from Fault Warming to Fire on their own?
Answer - An Auto Learn function was done with the devices not connected to the bus. When re-connecting the points to the bus, the panel views these devices as new devices to be added. To reactivate the devices on the bus, an Auto Learn function needs to be done. This sets the point Action to defualt (FIRE) because the panel is adding them as a new device.