We have 40 to 50 panels on this campus all sending random data loss problems to the Central Station. The panel history confirms this. Why is this happening?
All the test timers were set for 2 AM default value and the Central Station could not talk to all 50 panels every night at 2 AM. Causing some of the panels to send a data loss to the CS.
DATA LOSS occurs when the panel dials all 10 attempts to the CS and cannot get it signal thru to the CS.
The fix is to stagger the Timer Test report at each panel.
Part numbers FPD-7024, D7024, DS9400, DS9400I, DS9400M,