How can the relay outputs on a 2000 Series panel be tested to make sure they work?
Putting the Keypad into the Diagnostics Mode
The panel sends SERVICE START and SERVICE END messages upon entering and exiting Diagnostics Mode.
1.) Lock the Standby Switch down.
2.) Press the  key on the keypad.
3.) Enter your "Installer" passcode.
The default Installer passcode is 654321. The default passcode length is three, so if you have not changed the default entries, press   .
If the passcode you have entered is valid, the keypad’s display scrolls the functions that are available.
Now that you are in...
When you select a function, the system displays messages informing you of test status. Once inside a function, press the [Clear] key to return to the previous level.
The Relays function can activate either of the two external relay outputs.
1.) Press the  key to enter the Relays function.
2.) Hold the  key to turn on relay 1. The relay stays on as long as key 1 is held down. Follow the same procedure to test relay 2.
3.) Press the [Clear] key to exit this test.
Part numbers D2212, D2212B, D2212BE, D2412, D2412U, D2412UE, D2812, D2812U, D2812P, D222A, D223A, D202A, D220A