7000/9000 Series panel types thru GV3 panel types:
Connect the DX4010i or DX4010V2 to the SDI Bus. 7000/9000 and G tyes must use terminals 29-32. GV2 and GV3 types can use the 4-pin molex connector labled SDI or the 4-pin molex connector labeled SDI.
GV4 panel types:
GV4 Panel types have connections for both the SDI and SDI2 bus. SDI and SDI2 are different types of busses, the DX4010V2/DX4010i will only work when connected to the SDI bus. Connect the DX4010V2/DX4010i to either the 4-pin molex connector labeled SDI or use terminals 29-32.
When addressed and connected correctly to a compatible panel, the red LED will flash at a 1/2 second rate.
The Installer Switch must be Closed / Locked on D4412 or D6412 panel types in order to connect to RPS.