How can a REX sensor such as the DS150i or DS160 be used to shunt an armed point?
The REX sensor can be used to shunt a normally closed contact by connecting the REX relay contacts that will provide closure when motion is detected in parallel with the door point to be shunted. When these contacts close, a short will be placed across the door point. The panel will see the door as closed for the duration of the REX relay time.
Note: The REX relay Common to Normally Open and Common to Normally Closed contacts will reverse when changing from Fail Safe to Fail Secure mode. See NOTES for further clarification.
In Fail Safe mode, use the Yellow and Violet wires on the first relay or the Gray and Green wires on the second relay.
In Fail Secure mode, use the Yellow and Blue wires on the first relay or the Gray and Orange wires on the e second relay.
In Fail Safe mode, use the relay contacts designated Normally Open to Common.
In Fail Secure mode, use the relay contacts designated Normally Closed to Common.