Use the D8129 with the 8112 Series D8129 Operation and Installation 1 Zone Status Mode (Switch Settings: 1 = ON, 2 = ON, 3 = ON, 4 = OFF).
The Zone Status Mode provides a relay output each time a protective zone is faulted, in alarm, shunted or force-armed. Each relay output has the same identifying number as its corresponding zone.
Zone Condition Relay Response Faulted Relay activated by a faulted zone provides a steady output until fault is cleared.
Alarm Relay activated by an alarm condition provides a rapid pulsing output and remains active until Command 4 is entered or until the arm/disarm passcode is re-entered.
Shunted or Force Armed A relay activated by a zone that has been shunted provides a slow pulsing output.
Zone Conditions and Relay Responses D8112:MAIN, Program Item 103 SHOW must be programmed YES in order for the Zone Status Mode to operate properly. Also note that the Response/Condition for each relay output should be the same in the Zone Status Mode. Relay # Response/Condition 1 to 8 Steady output for Zone fault, or rapid pulsing output for Zone Alarm, or slow pulsing output while Zone is shunted or force-armed.