When using Wheelock / Cooper / Eaton Exceder LED 3 Strobes and Horn Strobes on a UL Listed Bosch Fire panel a DSM or SM Wheelock Sync Module is required. The Wheelock protocol built into the panels listed below do not support the newer Exceder LED 3 product line at this time.
The Exceder LED 3 Product Line is not UL Listed Compatible with UL Listed Bosch Fire Panels
FPA-1000; FPA-1000-V2 (Firmware less than 2.02)
FPD-7024 (Firmware less than 1.06)
FPP-RNAC-8A-4C (Firmware less than 1.10)
DS9400; DS9400I; DS9400M; D7024; FPD-7024; FPP-RNAC-8A-4C-(Never the product is End of Life)