When using Wheelock / Cooper / Eaton Exceeder LED 3 Strobes and Horn Strobes on a UL Listed Bosch Fire panel a DSM or SM Wheelock Sync Module is required.
The Wheelock protocol built into the panels listed below do not support the newer Exceeder LED 3 product line at this time.
The Exceeder LED 3 Product Line is not UL Listed Compatible with UL Listed Bosch Fire Panels
FPA-1000; FPA-1000-V2 (Firmware 2.02 and lower)
FPD-7024 (Firmware 1.06 and lower)
FPP-RNAC-8A-4C (Firmware 1.10 and lower)
DS9400; DS9400I; DS9400M; D7024; FPD-7024; FPP-RNAC-8A-4C-(Never the product is End of Life)
Valid as April 2020