In RPS panel programming - User Configuration > User (Keypad) Functions > Walk Test All Fire Point
Walk Test All Fire Points
Disable (-) - Disable this function panel wide regardless of the user's authority leve
Enable (E) - Enable this function panel wide without requiring a passcode.
Passcode (P) - Require a passcode to enable this function panel wide.
This parameter disables, enables without passcode required, or enables with passcode required, the Fire Walk Test user function and the Fire Drill function (DRILL key on B925F & B926F keypads).
The Fire Walk Test includes fire points and gas points. Controlled points and 24 hour points cannot be tested using this Fire Walk Test.
When a Fire Walk Test starts
The control panels sends a FIRE WALK START report to the central station receiver.
There is local alarm annunciation only, no alarm reports are sent to the central station receiver. The control panel is powered by the battery only. The Fire Bell output activates for 2 seconds for each fire point or gas point that is tested.
All fire points and gas points with the Resettable parameter set to YES, automatically reset when tested. [SENSORS RESETTING] shows at keypads.
The keypad shows the point text for each point as each it is tested, and an updated "points tested" count.
The test ends after all points are tested or after 20 minutes of no activity. The control panel sends a FIRE WALK END report to the central station receiver.
If fire points or gas points are faulted when Fire Walk Test ends, the points are bypassed and the trouble tone sounds. The keypads show the bypassed points and the trouble condition.
When a Fire Drill starts
The control panel sends a FIRE DRILL START report to the central station receiver.
The Fire Bell output activates until a user ends the drill by silencing the Fire Bell.
Fire points and gas points are active. An alarm on a fire point or gas point ends the drill. The control panel sends Fire alarm reports.
When the fire drill ends, the control panel sends a FIRE DRILL END report
... View more
The keypad displays the Access Module Door Point is in trouble. Diagnostics displays the point as missing.
T+ (Tamper Input) of the Access Module is an unsupervised input that is normal when open. Upon a short, the Door Point number assigned to the supervised zone of the Access Module is reported as a MISSING PT###.
... View more
Can I keypad program the individual panels for networking them together?
From the panel keypad, press the ENTER [↵] key and navigate to 6-PROGRAMMING (enter the level 3 passcode, default = 3333), 8-NETWORKING, 1-NETWORK CARD and select 1-Installed from the menu.
Press 1-YES to indicate the networking card is installed. Press the ESC key twice.
Press 2-NETWORK WIRING and select 1-CLASS A or 2-CLASS B. Press the ESC key twice.
Press 6-TIMERS AND SYSTEM, 2-SYSTEM and select 5-PANEL IP AND ID from the menu.
Press 1-PANEL IP ADDRESS.
Input and record a unique IP address for the panel. Press the ENTER key once.
Press 2-PANEL GATEWAY.
Input and record the same Gateway (default = 192.168.1.1) for each panel to be added to the network. Press the ENTER key once.
Press 3-PANEL SUBNET MASK.
Input and record the same Subnet Mask (default = 255.255.255.0) for each panel to be added to the network. Press the ENTER key once.
Press 4-PANEL ID.
Input and record a unique ID from 01 to 64 for the Panel ID. Press the ENTER key once.
Press 5-FIRE NEWTWORK ID. Leave at (001) - DO NOT CHANGE NEWTWORK ID.
Select and record the same Fire Network ID for each panel to be added to the network (the default, 01, can be used for each panel). Press the ENTER key to save the settings and then press the ESC key four times to return to the Main Menu.
Press 6-PROGRAMMING, 8-NETWORKING, 1-NETWORK CARD and select 2-PORT SUPERVISION from the menu, select 1-YES - for each port (1, 2, and/or 3) that is being used and 2-NO if that port is empty.
Press the ESC key five times to escape from keypad programming.
Repeat steps 1 through 17 for each panel that will be added to the network.
After all panels have the above programming completed, perform the following. From the panel keypad, press the ENTER [↵] key and Press 6-PROGRAMMING (enter the level 3 passcode, default = 3333), 8-NETWORKING, 3-PANEL MANAGEMENT and select 1-ADD A PANEL from the menu – Enter the PANEL ID of each panel on the Network. Repeat this step on each panel.
... View more