Part Numbers for Flush Mount Smokes - FPC-500, FCP-500-C, FCP-500-P, FAA-500-BB-UL, FCA-500, FAA-500-TR-P, FSP-500, FCA-500-E, FAA-500-TR-W, and FCP-500-C-P. To make ordering easier please refer to the Product Data-Sheet and order the kit part numbers.
Perform these steps to enable the D7024, FPD-7024, DS9400, DS9400I, and DS9400M for RPS programming via phone line with a compatible RPS modem: Press (0) Enter Program Mode. Enter Pin (Default is 9876). Press (6) Accounts. Press (4) Ring Count. Set Ring Count to (02) #. Press the (*) key two times or until you see PROGRAM MODES. Press (3) System. Press (7) Remote Program. Press (1) Enable. Press the (*) key five times to Exit Program Mode. You need to dial Line 1 on the panel. It is the second line down on the panel (it is NOT the line in the top right). Before connecting with RPS, perform an Auto-Learn with at least one Mux Device connected to the Mux loop, then send your RPS program to the panel. Press (0) Enter Program Mode. Enter Pin (default is 9876). Press (9) Program Mux. Press (4) Auto Program. Press (1) Yes.
Listed in the table below you will find the old DS MUX Device part number with the new MUX Device replacement. Replacement Part Numbers Old DS MUX Devices Description FPE-7039, D7039 DS9331, DS9431R MUX Card D7050-B6 MXB2W MUX Base D7044 MX361 Single Point D7044M MX361M Mini Single Point FMM-7045 MX310 Pull Station FMM-7045D MX310D Dual Action Pull Station D7052 MX363 Dual Point Module D7053 MX46 I/O Input/Output Modules D7050 MX250 MUX Smoke Head D7050TH MX250TH MUX Smoke Head with 135 Heat Sensor .
Note: The Master - Slave application is used to save on popit addresses for a large systems. You can use one popit address for a long hall or one large room that would otherwise require several addresses to cover it. 1. The F220-B6PM is a 24 VDC 4-Wire Master Popited Base that supervises up to nineteen F220-B6 Two-Wire Slave Bases. The two-wire slave detectors then report as the master base address. 2. The F220-B6PS 4-Wire Popited Base operates on 12 or 24VDC that does not support 2-Wire Slave bases. 3. The F220-B6PS, F220-B6, and the F220-B6PM bases can use any of the following smoke or heat heads. F220-P - Photoelectric Smoke Detector F220-PTH - Photoelectric Smoke Detector with 135F/57C Heat Sensor F220-PTHC - Photoelectric Smoke Detector with 135F/57C Heat and Carbon Monoxide Sensors F220-135 - Electronic Rate of Rise/Fixed Temperature 135F/57C Heat Detector F220-135F - Electronic Fixed Temperature 135F/57C Heat Detector F220-190F - Electronic Fixed Temperature 190F/88C Heat Detector
Uses for the D298M over a D298S or D278S popited base? D278S 12 volt popit base. D298S 24 volt popit base. The D298M is a 24 volt popit base that provides connections for up to 19 supervised circuits two-wire slave detectors (D287 2-Wire Base with D285 Smoke Head or D285TH Smoke Head with 135 degree heat sensor) reporting to the master address. The D298M is used over the D298S to conserve popit addresses on a large system.
The FAA-325-B6S is to be used with the FAP-325, FAI-325 and FAH-325 model sensors only. The FAA-325-B6S provides an audible alarm in the immediate vicinity. Typical applications are for use in hotels, apartments, and hospitals. It is compatible with the FPA-1000, FPA-1000-UL, and FPA-1000-V2.
From RPS in the following panels DS9400, DS9400I, DS9400M, D7024, and FPD-7024 you have the option to set Anti-takeover Setting to one of the following. a.)Allow all local programming: All programming items may be accessed from the local keypad. b.) Lock phone/account numbers only: All programming except phone numbers and account numbers may be accessed from the local keypad. c.) Lock all local programming (except Date/Time and all user PINs): Allows only the Date and Time to be set from a local keypad.