Issue - Can the MUX data loop be run in the same cable of wire as the Keypad data wires? Solution - They cannot, they are two different data outputs. They should never be run in the same jacketed of wire. They each require their own wire run and should at least 3 inches apart in the raceway. Part numbers DS7400X, DS7400Xi, DS7400, DS7400XIVER3+, DS7400XIVER4+, DS7400XIVER2, DS7430, DS7436, DS7447
The FAA-325-B6S is to be used with the FAP-325, FAI-325 and FAH-325 model sensors only. The FAA-325-B6S provides an audible alarm in the immediate vicinity. Typical applications are for use in hotels, apartments, and hospitals. It is compatible with the FPA-1000, FPA-1000-UL, and FPA-1000-V2.
The D305 does not have the ability to trip the control panel or smoke head into alarm. The D305 Test Plate only toggles the alarm LED and relays of the D332A, FAD-325-R and FAD-325-V2F-R. The only way to get the control panel to display an alarm or supervisory from the Analog Hochiki DUCT Detectors is by using UL Listed canned smoke (refer to the testing procedure below). Currently the only work-around is to connect a single point module (D334A, D339A, FLM-325-IM, FLM-325-I4, FLM-325-I4-A or FLM-325-I4-AI) to one of the alarm relays of the D332A, FAD-325-R or FAD-325-V2F-R. *Note: If the customer installed the D331A, FAD-325, or FAD-325- V2F we have no way of using the D305 to trip the panel into alarm. Option 2 - Replace the DUCT Housing (D331A, D332A, FAD-325, FAD-325-R, FAD-325- V2, or FAD-325- V2-R) and Test Plates (D305) with D341P Conventional DUCT Housing with Head, D344-RT Remote Test Plate, and D339A, D334A, FLM-325-IM, FLM-325-I4, FLM-325-I4-A or FLM-325-I4-AI Analog Single Point Monitor Module. The downside is that the customer will lose the ability to read the sensitivity of the DUCT through the control panel web-browser. Testing Procedure (D331A, D332A, FAD-325, FAD-325-R, FAD-325- V2, or FAD-325- V2-R) Install the detector housing. The green Pilot LED on the housing’s front lights. Remove the head. The Pilot LED goes out to indicate head supervision. Replace the head and reset the FACP. Test the detector’s operation. Light a piece of clothesline and place it approximately 3 in. (7.6 cm) from the head. Blow across the lighted area toward the detector head. The Alarm LED lights within 1 min and the two alarm relays energize shorting Terminal 8 to 9 and Terminal 11 to 12. Reset the housing. The detector momentarily resets and returns to the alarm condition. Perform this operation several times. After 5 min, the smoke in the detector head clears and the detector remains reset. Replace the cover.
Listed in the table below you will find the old DS MUX Device part number with the new MUX Device replacement. Replacement Part Numbers Old DS MUX Devices Description FPE-7039, D7039 DS9331, DS9431R MUX Card D7050-B6 MXB2W MUX Base D7044 MX361 Single Point D7044M MX361M Mini Single Point FMM-7045 MX310 Pull Station FMM-7045D MX310D Dual Action Pull Station D7052 MX363 Dual Point Module D7053 MX46 I/O Input/Output Modules D7050 MX250 MUX Smoke Head D7050TH MX250TH MUX Smoke Head with 135 Heat Sensor .