The FPA-1000, FAP-1000-UL and FPA-1000-V2 all have the option to use 2 FPE-1000-SLC Loop cards. Each loop card on panel with Firmware less then 1.09 only support address 1 to 127 on each loop card, from firmware 1.10 and higher each loop card supports address 1 to 254. So it is possible to have to devices with the same address but on different loop cards. The the panel the keypad will display the following on the top line. The Event Type (Trouble, Fire, Supervisory) follow by XX-Y-AAA.A, (XX = Panel ID) (Y = Address Assignment, 0 - Web Page, 1 - SLC1, 2 - SLC2, Mainboard, or 4 - Option Bus) Followed (AAA.A The Device Address) .
Part Numbers for Flush Mount Smokes - FPC-500, FCP-500-C, FCP-500-P, FAA-500-BB-UL, FCA-500, FAA-500-TR-P, FSP-500, FCA-500-E, FAA-500-TR-W, and FCP-500-C-P. To make ordering easier please refer to the Product Data-Sheet and order the kit part numbers.
Panel part numbers - FPD-7024, FPA-1000, FPA-1000-UL, and FPA-1000-V2. Network Card part numbers for the FPD-7024, DX4020, B420, and B426. Cellular option for the FPD-7024 part numbers B450 (Interface for Cellular Card) B440, B441, B442, B443, and B444.
This article discusses how to send reports to the CS (Central Monitoring Station) from the FPA-1000-V2. We can network up to 8 of the FPA-1000-V2 panels together. Each panel can report to the CS by itself, or one panel can report for all. In either configuration, each panel needs its own unique account number.