The DataLock system uses lockcodes to lock panels from programming by unauthorized programmers. A Datalocked panel has a lockcode in memory that the 5200 must match to one of the lockcodes in the 5200 lockcode records before the programming session can continue. If 5200 cannot match the lockcode in the panel, the programming session is terminated.
I get to the FPA-1000 browser Start page. When I click on Login I get the following message: Invalid PIN - A PIN must be a 4 Digit number. Please check that Number Lock is On. What should I do?
Add the FPA-1000-UL IP address to the list of trusted sites, and your login will work correctly. A Crossover cable is required to connect directly to the panel.
Tools menu: Select Internet Options.
Select the Security tab.
In the settings for Trusted Sites, click Sites.
Add the FPA-1000-UL IP address to the list of trusted sites.
Listed in the table below you will find the old DS MUX Device part number with the new MUX Device replacement. Replacement Part Numbers Old DS MUX Devices Description FPE-7039, D7039 DS9331, DS9431R MUX Card D7050-B6 MXB2W MUX Base D7044 MX361 Single Point D7044M MX361M Mini Single Point FMM-7045 MX310 Pull Station FMM-7045D MX310D Dual Action Pull Station D7052 MX363 Dual Point Module D7053 MX46 I/O Input/Output Modules D7050 MX250 MUX Smoke Head D7050TH MX250TH MUX Smoke Head with 135 Heat Sensor .
When devices are connected to the Option Bus on the FPD-7024, the bus must be scanned allowing the panel to see the device. After removing devices, such as the DX4020, DX4010V2 or DX4010i, the option bus must be scanned again to complete the removal, or the panel continues to supervise the device resulting in a keypad display: Trouble DX4020 and history event: SYSTRB017.
After completing programming the panel reports trouble DX4020; history shows SYSTRB017
After removing the DX4020, DX4010V2 or DX4010i, the option bus must be scanned again to complete the removal or the panel continues to supervise the device.
From the Panel Keypad (not a remote keypad) perform the following steps to update the option bus:
Select 0 for PROGRAMMING and enter the installer code
Select 3 for PROGRAM SYSTEM
Select 4 for OPTION BUS
Select 1 for UPDATE BUS
Part Numbers for Flush Mount Smokes - FPC-500, FCP-500-C, FCP-500-P, FAA-500-BB-UL, FCA-500, FAA-500-TR-P, FSP-500, FCA-500-E, FAA-500-TR-W, and FCP-500-C-P. To make ordering easier please refer to the Product Data-Sheet and order the kit part numbers.