The D8112 panel is not sending signals when modem format is selected to the Central Station.
Only the D8112G2 can send signals in Modem II format with a CS setting of 7.
The D8112E, D8112E1, D8112G, D8112G1 and D8112A must have CS set to either Blank or a selection between 1 and 6 but not 7.
Only Modem Format can report a 4 digit account number to the Central Station all others only report a 3 digit account number.
How many Logger Events can the D8112G2 store?
The D8112G2 Control Communicator can store up to 400 Events in the panel memory. The panel logs the time, date, event, master zone, and the primary or alternate phone number called for each event. The 400 events can be retrieved with the RAM II, RAM IV or RPS downloading software.
What are the enviromental considerations for the proper operation of the Bosch control/communicators?
Relative Humidity 5% to 85% noncondensing at +86 degrees Fahrenheit (+30 degrees Celsius).
Operating temperature would be +32 degrees Fahrenheit to +120 degrees Fahrenheit ( 0 degrees Celsius to 49 degrees Celsius ).
Why does the zone light on the D360 Command Center light when the D279A is disarmed?
The D8112 panel is programmed with a zone code of 3271 on a particular zone. The purple jumper on the D279A is cut. As a result, the D360 zone light illuminates when the D279A is disarmed.
This is normal and will not impact the D8112 arming process. If the D1252A is used, the disarm state of the D279A is not indicated.
How to correct the D8112/5505 not sending a Reboot report.
The 8112/5505 panel is communicating alarm and trouble signals but after resetting the panel it does not report the reboot.