What are the enviromental considerations for the proper operation of the Bosch control/communicators?
Relative Humidity 5% to 85% noncondensing at +86 degrees Fahrenheit (+30 degrees Celsius).
Operating temperature would be +32 degrees Fahrenheit to +120 degrees Fahrenheit ( 0 degrees Celsius to 49 degrees Celsius ).
How to interpret the 'Check Device' display on a D1255 or D1260 keypad.
Why does the keypad display "Check Device"?
How to locate which point generated the 'Check Device' display and modify programming to prevent the display.
Does Max Number of B208 Limit the number of B308's that can be used?
Does Max Number of B308s Limit the number of B208 's that can be used?
The maximum number of B208 modules and B308 modules that are available to the panel type can be connected at one time.
The only limit would be available power and SDI2 cable distance specifications which are detailed in the module documentation as well as the panel Installation and System Reference Guide (ISRG).
The B-Series panel onboard relay can be configured for either:
Standard Form-C relay
Aux Power configuration, Right two pins covered, the C terminal has 12Vdc available and upon activation will switch to the NO terminal.
Relay A turned off, NO to Common reads 0Vdc. Relay A turned on, NO to Common reads +12Vdc.
Aux Common configuration, Left two pins covered, the C terminal is Common. Upon activation Common is switched to the NO terminal.
Relay A turned off, NO to Aux= 0Vdc Relay A turned on, NO to Aux= 12Vdc
Dry Contact Configuration No jumper used, NO and C and NC works as a standard dry contact.
Relay A turned off, NO to C= Open, NC to C= Short Relay A turned on, NO to C= Short, NC to C= Open
How to address SDI2 devices without causing address conflicts.
Can different types of SDI2 devices use the same address setting?
B810, RFRP-A, B820, B208, B308, B420, B426, B520, B920, B921C, B930, B942.
The D5200 needs to match a Data Lock code in the panel to access programming. Changing the panel Data Lock Code from the default of 12345 will prevent access.
Remote Programming Software:
RPS also needs to match the Data Lock code in the panel to access programming. Changing the panel Data Lock Code from the default of 12345 will prevent access.
RPS also needs to match the RPS Passcode (or RAM Passcode in legacy types) in order to allow access programming. Changing the default from 999999 will block RPS access.
Using RPS software, how can an existing panel program be upgraded to a new higher version program without having to re-enter the individual program parameters under the new panel type?
D7412G,D9412G,D7212,D7212B,D7212B1,D7212G,D7412,D9112,D9112B,D9112B1,D9412,D9412GV2,D7412GV2,D7212GV2,RAMIV,RAMIV LITE,RPS,RPS LITE,D7212GV2,D7212GV3,D7212GV4,D7412GV2,D7412GV3,D7412GV4D9412GV2,D9412GV3,D9412GV4 Version 1