How to configure the output in GV4 ver.2?
Selections: 0 to 8 (increments of 1)
Use this parameter to activate an output when the point goes into alarm.
The output does not activate for Trouble nor Supervisory events. Reset the output by clearing the memory from the keypad display.
The outputs used can be on an output module installed on either the Zonex bus or the SDI2 bus.
*Notice that the Relay will activate only when the point goes in to alarm, not when it changes to an off-normal state.
Follow the steps from this article to accomplish the BFSK relay functionality.
If there is no G in the panel's name, there is no ground fault detection and the panel does not have an S4 pin.
If it has a single G in the name it has the chance it could be enabled if S4 is latched and under area 5 silent alarm relay there is a value other than 0.
If it’s a GV2, GV3 or GV4 and S4 is latched, ground fault detection is enabled.
If there is ground fault detection, latch S4 and measure DC voltage on Terminals 9 and 10: You should get 6.5-6.8 VDC Steady (not jumping around) when there isn't a ground fault.
If there is a ground fault it can take up to a minute to display and clear at the keypad.
The heartbeat LED on the B426 is off.
No communication failure, trouble or communication module missing error messages at the keypad.
Check the TMPR pins next to the Ethernet port on the B426.
Remove the jumper from the pins; the B426s heartbeat LED will start flashing to show the firmware version on the board and then it will resume normal or trouble operation depending on the condition on the B426.
When the Tamper jumper is covering both pins the heartbeat LED is turned off to save power.
How to configure Door Control on both sides of a door with B8512G, B9512G or B6512 panels.
How to configure Door Control for Card-In and Card-Out with B8512G, B9512G or B6512 panels.
How to configure Access Control for Card-In / Card-Out with B8512G, B9512G or B6512 panels.
What are Point Profiles and how are they used to program points on B8512G/B9512G or B-series panels?
How to program the B3512.
How to program the B4512.
How to program the B5512.
How to program the B6512.
How to program the B8512G.
How to program the B9512G.
This article demonstrates how to enable the Telnet password and secure the D6686 IPv6 Communicator from Internet based attackers, attempting to utilize the second available tunnel.
How to return the D6686 to factory settings.
How to determine which antenna to use with the B444 or B440 cellular cards.
What is the difference between the B440 antenna and the one used by the B444?
Can the antenna from the B440 be used on the B444?
How to determine which wireless interface to use with the EN1224-ON keyfob.
How to determine which control panels the EN1224-ON keyfob can be used with.
Is the EN1224-ON compatible with D7212 panel types (G, GV2, GV3 or GV4)?