When the D928 is installed, the control panel alternates between Phone Line 1 and Phone Line 2 to send its first report. For example, on Day 1, the control panel attempts to communicate on Phone Line 1. On Day 2, the control panel switches and attempts to communicate on Phone Line 2. When the control panel is reset or powered on or off, the next reported event always attempts to call out on Phone Line 1 first. If Phone Line 2 (secondary) is not in service on Day 2, the control panel switches to the primary phone line to send the report.The Bosch Security System control panels use the D928 Dual Phone Line Switcher to transmit over a second phone line when the primary phone line has a fault. The control panel monitors the primary line and the D928 monitors the secondary line. If a signal is generated and the control panel senses that the primary phone line is bad, it will attempt to use the secondary phone line to send the message.
Part numbers D7212B, D9112B, D7212B1, D9112B1, D7212, D7412, D9112, D9124, D9412, D7412G, D9124G, D9412G, D7412GV2, D9124GV2, D9412GV2, D7412GV3, D9412GV3, D7412GV4, D9412GV4, D928,
When a fire alarm occurs, the control panel activates Relay A (Terminal 6), providing the trigger input to the “Horn” D192C/D192G. The output from Relay A also changes Point 3’s voltage to 5.0 VDC (electrically, an open condition caused by the 2.4 k. resistor), causing an alarm (burg alarm) condition. This activates Relay B (based on the Summary Alarm Relay programming shown above). Relay B provides the trigger voltage for the “Strobe” D192C/D192G. When the Fire Alarm is acknowledged at the command center, power is no longer applied to Relay A causing the horns to silence and returning Point 3 to a normal state of 2.5 VDC. However, Relay B continues to stay activated until alarm memory is cleared at the command center by using Command 4 or entering Passcode + [ESC]. After the Fire Alarm is acknowledged, the command center first scrolls the fire alarm points, then scrolls AREA 1 1 ALARMS. This occurs because Point 3 is a Burg Point. Once a Command 4 or a Passcode + [ESC] is entered, the Alarm Memory is cleared.
Part numbers D192C, D192G, D7212, D7412,D9112, D9124, D9412, D7212G, D7412G, D9112G, D9124G, D9412G
The Timer Test is not coming in. The panel history shows Off Normal Test. The panel is programmed to send all reports in CID. Central does not see an E608 CID report for an off normal test.
Contact ID Reporting. The system can be programmed to send a periodic test report, E602, in Contact ID format. If any system troubles are present at the periodic test time, a new event, E608, which states “New event, off normal at time of periodic test report” is sent. Software versions 2.03 and before sent a generic system trouble P300 report.
Part numbers DS9400, DS9400I, DS9400M, DS9431, D7024
Control trouble # 87 displays Battery Trouble.
The battery failed a battery test
The battery is defective
The wiring to the battery is disconnected
If there has just been a power failure, wait a least 24 hours for the battery to recharge, then perform a system reset to re-test the battery and clear the error
Replace the battery.