Panel controller displays can become de-calibrated, e.g. upon initial power-up followed by unintentional contact with the display or inaccurately touching the crosshairs.
It becomes noticeable after the panel controller has re-booted and does not respond properly to touch.
This article provides instructions for exporting and saving the program from an FPA-1000 to be imported into a replacement FPA-1000 panel.
This information may be needed when replacing an FPA-1000 fire panel with another with intentions to use the same panel program.
Do Bosch addressable smokes and smoke bases support CleanMe functions?
Currently the only Bosch smoke detector that supports CleanMe functions is the F220 series smoke heads when used with a conventional two-wire (F220-B6) base only and a CleanMe enabled control panel such as the D7024, and FPD-7024 conventional zones.
Note: The D7050, D7050TH does have a Chamber Check feature that will report dirty smoke if the head needs cleaning when used on the D7024, FPD-7024, DS9400m, DS9400, DS9400i.
The goal is to have a fully illuminated field of view for the installed AVIOTEC/s. Testing is required for every installation to make sure, that the area is illuminated correctly with full coverage and no reflections, aberrations or other.
If the Item "Panel" is e.g. 1-1.1.1 respectively 1-1.SI_PANEL.1,then this item is the Group item of the panel system status items e.g. 1-1.1.1-1 till 1-1.1.1-10.
Most of these system status items have NORMAL as value after startup, others can have ON, e.g. items from Condition Monitoring.