How to interpret the 'Check Device' display on a D1255 or D1260 keypad.
Why does the keypad display "Check Device"?
How to locate which point generated the 'Check Device' display and modify programming to prevent the display.
AC Fail/Res Rpt
Parameter Description: AC Power Supervision reports are sent to the central station and local printer at the time programmed for AC Fail Time.
IMPORTANT: To comply with NFPA standards and UL 864 requirements for Commercial Fire Systems, program this item NO and program AC Tag Along as YES.
Yes: Send AC Fail and AC Restoral reports.
No: Do not send AC Fail and AC Restoral reports.
1) Receive copy of 9000MAIN
2) Enter group PANEL WIDE PARAMETER
3) Enter group Power Supervision
4) Fail/Res Rpt Yes/No (SPACE bar to change)
*Must press ENTER for each prompt entry
5) Send Load to panel
An FA400 receiver that is disconnected will not force the keypad to display a missing message.
If two FA400 receivers are being used on the same D8125INV, the "Receiver Missing" message will not display if only one of the receivers is disconnected.
The keypad will display ‘Command Disabled’ when the Menu key is pressed for one of the following reasons.
If the menu item # 1 in the function list is set with a function 0 and marked yes for any Command Center.
If all of the Functions for the Command Center are selected as No (disabled).
To prevent the keypad from displaying ‘Command Disabled’ after selecting Menu;
Select a non-zero value for the Function # of Menu Item 1.
Ensure that at least one of the Menu Items intended for use are set as Yes.
How to activate multiple auxiliary relays on Area Wide or Panel Wide Events.
Programming Area Wide or Panel Wide Relays will only allow a single relay entry. Use an auxiliary relay such as the D130, D133 or D134 when multiple relays are needed to energize on a panel event.