How can the rising sun key or trapazoid key be used to activate an output on the D4412/D6412 control communicator?
Under Output Parameters, program a 1,15 for the trapazoid key or 2,0 for the rising sun key to activate an assigned output when the keyfob's alternate buttons are depressed.
Overview: The Inovonics FA570 and FA575 High-Power Repeaters receive, decode and re-transmit signals from Inovonics FA-Series transmitters up to 4 miles in open field.
What is the difference between the FA570 and FA575?
The difference is the FA575 includes the ACC640 weatherproof enclosure to accommodate exterior applications as well as battery leads to hookup an external battery. Other then that, the units are exactly the same.
When does the D128 dual phone line switcher module indicate a phone line failure?
An amber phone line status LED lights on the D128 module when the control/communicator measures less than 25VDC or 10mA of current across the tip and ring of the telephone line. The D8112 and D9112 monitor the telephone lines for a programmable interval before indicating a trouble condition.
What would cause the D6112 panel to send a zone 9, when arming the system?
D5200 Programing - 7.10 or 8.10 = Comb ID is set to yes in the program of the panel. With this
prompt set to yes in the program, a zone 9 is sent when the panel is armed
by the remote programmer, or command 1.
Overview: Charging circuit is overcharging the battery. Panel is damaged.
Reading 15vdc on the battery charging circuit.
Replace the panel. The voltage regulator is failing on the panel.
Overview: D4112 doesn’t arm or anything when code is entered at the keypad.
Nothing happens. Doesn’t arm or anything when code is entered at the keypad.
Connect programmer using coiled cord.
Plug in plastic RJ phone type plug into COMMUNICATOR female connector on 5200
Plug brown connector on other end of coiled cord to programmer connection on 4112
Press ON button on 5200
Type in password at PASSWORD prompt, press enter.
Top Line of 5200 shows PRODUCT HANDLERS
Using the up/down arrows scroll down until 4112. Please blinking cursor on 4112
Press RED Enter Group button
Place cursor on NEWRECORD
Short the Standby pin on 4112 to ground momentarily
Press RECV(COPY) button on programmer
Receiving will be displayed at the top line of the 5200 Display
Scroll down using arrow down key until cursor is on 2 PASSCODES
Press ENTER GROUP button
Passcode1 should have 234 in the field.
To change field, press CLEAR key and type in the code to be used.
The code is restricted to 4 characters but the user enters a prefix of 1, 2, 3, 4, 5…depending upon the slot. Example: PASSODE1 shows 234. The user code will be 1234
*** NOTE: Also make sure that the panel has a valid and functioning analog line. The functionality of the system is dependent upond successful communications.
On 2000 series panel, point codes are programmed for points between 9 and 24. When programmed points are tested the keypad reads "PT(#) PT DISABLED (where # is the number of the point being tested).
Pt text (Point Text) was never changed from default that read "PT(#) PT DISABLED".
How many zones is the D4112 Control Communicator capable of having?
The D4112 Control Communicator has six end-of-line resisitor supervised, hardwire protective zones. There are five standard programmable zones and one nominal 12 VDC powered zone optimized for two-wire smoke detectors