Possible causes and solutions:
Ground Fault Detect enabled
The control panel has a ground fault detection circuit that when enabled, detects ground faults on Terminals 1 to 9 and 11 to 30. If a ground fault condition occurs, the keypads annunciate a ground fault and control panel transmits a trouble message.
Ground Fault condition is corrected
When the control panel recognizes that the ground fault condition is corrected, and remains corrected for between 5 to 45 consecutive seconds, the control panel clears the fault from the keypad display and sends a restoral report
Measure earth ground (Terminal 10) and COMMON (Terminal 9) to determine whether the control panel has the necessary 0 VDC decay to -2.1 VDC. Measuring and comparing voltage for ground fault detection:
Set your digital voltmeter (DVM) to measure VDC.
Connect the red DVM lead to control panel Terminal 10, and the black DVM lead to Terminal 9.
Compare this voltage to the following table:
Enable Ground Fault Detect and reports
To enable fault detection, use RPS. Set the following parameters:
· PANEL WIDE PARAMETERS > Miscellaneous > Ground Fault Detection. Set to Enable
· PANEL WIDE PARAMETERS > Report Routing > Burglar Reports > Trouble Report. Set to Yes.
· PANEL WIDE PARAMETERS > Report Routing > Burglar Reports > Burg Restore (After Trouble). Set to Yes.
How can the command center be cleared after an alarm condition on the 7000/9000 series panels?
How to determine which antenna to use with the B444 or B440 cellular cards.
What is the difference between the B440 antenna and the one used by the B444?
Can the antenna from the B440 be used on the B444?
What are Point Profiles and how are they used to program points on B8512G/B9512G or B-series panels?
How to program the B3512.
How to program the B4512.
How to program the B5512.
How to program the B6512.
How to program the B8512G.
How to program the B9512G.
How to configure two readers to a single door, one to enter through a door and a second to exit through the door. Access Control, Reader, Door, Enter, Exit, Card, Egress, D9210B, D9210C, D7412, D9412, D7412G, D9412G, D7412GV2, D9412GV2, D7412GV3, D9412GV3, D7412GV4, D9412GV4
Is the EN1212 compatible with G or B series panels? ISW-D8125CW-V2, D9412GV4, EN4200,B820,B3512, B4512, B5512, D7212G, D7412G, D9412G, D7212GV2, D7412GV2, D9412GV2, D7212GV3, D7412GV3, D9412GV3, D7212GV4, D7412GV4, D9412GV4, EN4200, B820