Unable to use Command 00 function. When CMD 00 is entered, keypad reads 'SYSTEM COMMAND' or 'INVALID KEYS'.
Un-Bypassing points on the D7112 panel must be done by using the FUNCTION Menu. Access the Function menu by pressing 'Enter' at the idle disarmed text. Press Next repeatedly until Function Menu displays. To access the UNBYPASS screen press enter on Function menu and Next until UNBYPASS displays. Display will read ENTER POINT NUMBER, enter the point number to be bypassed and press Enter. Display will read the text for the point, press enter again and screen will read POINT UNBYPASSED.
What is the force arm or bypass max on the DS7100?
The bypass max is only limited by point programming, if the point is programmed in data digit 3 as bypassable then it may be bypassed no matter how many other zones may also be bypassed while arming.
Is there a list of commands for the DS panels?
DS7090, DS7090I, and DS7100
Command 1 Arm All
Command 2 Instant Arm
Command 3 Delay Arm
Command 4 Custom Arm
Command 5 Custom Arm
Command 6 Custom Arm
Command 7 Alert Mode (chime mode)
Command 9 Zone Bypassing
Command 81 Area Test
Command 89 History
Command 89* History Reset
Command 80 Battery Test
Command 82 Communicator Test
Command 80 Fire Reset
Command 84 Indicator Light and Display Test
Command 83 Remote Program Dial Out
Command 86 Remote Program Answer
Command 85 Siren Test
Command 87 Trouble Display
Command 87* Trouble Display Reset
Unable to enter into program mode whether using a passcode or shorting out the solder pins, and the panel is not locked out of programming mode.
Make sure the panel does not have a ground fault issue. The best way to tell is to check the following:
Take a voltage reading from aux power positive to Earth ground.
The voltage should read - 6.7VDC.
If the voltage is lower or higher than -6.7VDC, a ground fault is present.
The panel may indicated this trouble if it is turned on.
If the voltage is 0VDC - the ground fault condition is on the positive side of the panel
If the voltage is 13 VDC then the ground fault is on the negative side of the panel.
Leave the volt meter accross the terminal and start disconnecting wires until the voltage goes to -6.7VDC
Overview: Firmware Revision 3.57 is NOT compatible with the D7112 panels with a date code of X9416 or higher.
Panel is non responsive to any programming.
Firmware Revision 3.57 is NOT compatible with the D7112 panels with a date code of X9416 or higher.
How does the phone line monitor for the DS7100 operate?
If the monitor detects a phone line fault for more than 50 seconds, the power LED will begin to flash. If the audible output has been enabled in line 89, the keypad sounder will pulse every ten seconds if the control is disarmed. If the panel is armed, the siren output will activate.
To ascertain if the trouble condition is indeed a phone line failure, enter # 87 at the keypad. The display will indicate "Communication Failure".
If the "System Trouble Report" (line 51) is programmed the system will try to send this report.
A phone line failure may be caused by:
A cut or missing phone line.
A reversed connection (Tip, and Ring Reversed)
A miswired jack
To clear the error;
Determine the cause of the failure and eliminate the cause.
After eliminating the cause of the failure, wait at least ten seconds.
The error will clear if the problem has been eliminated and the LED will stop flashing provided a failure has not occurred on the central station phone numbers. If a failure has occurred at the central station restore by entering # 87 * at the keypad.
D7112 Panel battery will not hold a charge.
A slow flashing (1 sec on, 1 sec off) yellow LED with the green CPU LED off indicates a power supply overload condition. The panel detects the battery as missing and the power supply cannot meet the power demand of the devices on the panel. The panel is shut down.
How is the phone line monitor turned on or off in programming?
DS7100 version 5.03 or higher.
The phone line monitor feature has been enhanced to provide output to allow enabling or disabling of the featrure through programming and to automatically reset after the phone line is restrored.
The feature is controlled in data digit 2 of program address 89.
To enable the phone line fault monitor without an audible output, program line 89 as 0200.
To enable the phone line fault monitor with a keypad warning beep when the system is disarmed and siren output when the system is armed, program line 89 as 0600.
To disable phone line fault monitor program line 89 as 0000.