How to determine which wireless interface to use with the EN1224-ON keyfob.
How to determine which control panels the EN1224-ON keyfob can be used with.
Is the EN1224-ON compatible with D7212 panel types (G, GV2, GV3 or GV4)?
How to determine the values to enter for the Poll Rate and Ack Wait Time.
Note: The calculation described is only be required on legacy control panels. The B8512G/B9512G and GV4 types only need a Receiver Supervision Time selection. The Poll Rate, Ack Wait and Retry count will automatically populate.
The formula for determining Poll Rate and Ack Wait Time is as follows:
Panel setting: Poll Rate + Ack Wait + ( Retry Count X Ack Wait)
Receiver setting: Panel Poll + Ack Wait
Panel setting = Receiver setting
Example: Panel Setting: Poll Rate = 240; Ack Wait = 10; Retry Count = 5 Panel setting: 240+10+ (5 X 10) = 300
Receiver Settings: Poll = 240; Ack = 60 Receiver setting: 240 + 60 = 300
300 = 300 Refer to the the following site for more information on setting up Conettix Devices
How to arm or disarm a single area using a keypad with scope in all areas.
When all areas are disarmed, associate areas can be armed independantly. But when attempting to disarm, associate areas keep rearming instead of disarming.
When leads to the battery are removed, the panel does not generate a low battery report.