Device Comm Error displays on the keypad. Reports trouble zone 2.
Wiring issue with the devices.
Device Comm Error displays on the D636 keypad. CS is receiving a Trouble zone 2 signal.
The devices (D636, D620, D640) have a wiring issue.
All device data wiring should be connected in series.
Example: Data wire out from panel terminal 11 to the first device
What are the SDI addresses on the D6412 and D4412?
SDI Address Device Description
0 = Installer Keypad, or local connection to RAM IV
1-8 = Command Center 1 to 8
40,41 = DX8010 Telephone Control Module
50,51 = RF Receivers 1, and 2
52-55 = RF Keypads on RF Receiver 1
60-63 = RF Keypads on RF Receiver 2
101-107 = DX 2010 wired point expander
150-151 = DX 3010 Octo-Output expander
250 = DX4010 Serial RS-232 Interface module
Can the D125B be Used to Power 2 Wire Smokes on the D7112?
Yes, see technogram number (73-06116-000-C) 1993 (attached). Listings and Approvals Underwriters Laboratories lists the D7112 ControVCommunicator as a Digital Alarm Communicator Transmitter (DACT) for: NFPA 71 Central Station, NFPA 72 Chapter 6 Local, NFPA 72 Chapter 8 Remote Station, NFPA 74 Household Fire Warning. The D7112 also has the following Approvals: CSFM and NYC-MEA (formerly NYC-BSA).
Using RPS software, how can an existing panel program be upgraded to a new higher version program without having to re-enter the individual program parameters under the new panel type?
D7412G,D9412G,D7212,D7212B,D7212B1,D7212G,D7412,D9112,D9112B,D9112B1,D9412,D9412GV2,D7412GV2,D7212GV2,RAMIV,RAMIV LITE,RPS,RPS LITE,D7212GV2,D7212GV3,D7212GV4,D7412GV2,D7412GV3,D7412GV4D9412GV2,D9412GV3,D9412GV4 Version 1
When I click on connect in RPS it brings up the standard connect window but the connect button is Greyed out and it will not allow me to call the panel.
RAMIV,RAMIV LITE,D5500C-USB,RPS,RPS LITE,D5500C-LPT
When trying to send or receive with a handheld programmer, or trying to connect with any version of RAM, invalid datalock is indicated.
RAM IV - D5370,RAMIV,RAMIII,RAMII,RAMIV LITE,RAM,RPS,RPS LITE,D5200
How long does a keypad message stay on the the keypad when it was sent from RPS or RAM IV Diagnostic Mode?