The B942 keypad will display the number pad. The keypad display screen will also alternate between Please enter installer passcode and SERVICE MODE. To exit Service mode, press and hold the reset button until the blue heartbeat led stops flashing. The panel will reboot and the B942 will resume normal operation.
Bosch Security Knowledge Base Unable to connect via USB - I have been connecting and programming the panel through the USB connection all day. Bosch Security Knowledge Base Related Products · B3512, B4512, B5512, B3512E, B4512E, B5512E, RPS 5.19, RPS-LITE 5.19, B99
The B8512 or B9512 supervises keypads even when disabled Related Products B8512 B9512 B915 B920 B921C B925F B926F B930 B942 Overview Issue The B8512 or B9512 supervises keypads even when Supervision=NO Solution If the keypad Type is set to an SDI type keypad (see below) the supervision setting can be configured YES or NO. When the keypad Type is set to one of the SDI2 type keypads the supervision Yes/No setting is ignored and the keypad is supervised. SDI2 devices are always supervised by design regardless of the supervision setting. SDI Keypads SDI2 Keypads D1255 VFD Keypad (SDI) B915 D125xRB Keypad (SDI) B920 D126x LCD Keypad (SDI) B921C B925F B926F B930 B942 Notes SDI2 devices that are the same type of device must use different addresses. SDI2 devices that are not the same type can be configured to the same address. For example: The B915, B92x, B930 or B942 are all same device types (keypads) and must use different addresses. The B920, B208 and B520 are all different device types and can all use the same address.
Bosch Security Knowledge Base How long will the C472 stay keyed up before they stop transmitting and how long does the transmitter have to wait before it can send signals again? C472, Multilink, Fastlink
The B8512G and B9512G have slots for two B430 Plug-in Telephone Communicators to provide redundant telephone connections. Upon power up the panel uses the B430 in the Mod-1 slot until a Test Report is initiated or when the panel phone supervision declares the line currently in use as failed. B430, B8512G, B9512G