Using RPS software, how can an existing panel program be upgraded to a new higher version program without having to re-enter the individual program parameters under the new panel type?
D7412G,D9412G,D7212,D7212B,D7212B1,D7212G,D7412,D9112,D9112B,D9112B1,D9412,D9412GV2,D7412GV2,D7212GV2,RAMIV,RAMIV LITE,RPS,RPS LITE,D7212GV2,D7212GV3,D7212GV4,D7412GV2,D7412GV3,D7412GV4D9412GV2,D9412GV3,D9412GV4 Version 1
What are the enviromental considerations for the proper operation of the Bosch control/communicators?
Relative Humidity 5% to 85% noncondensing at +86 degrees Fahrenheit (+30 degrees Celsius).
Operating temperature would be +32 degrees Fahrenheit to +120 degrees Fahrenheit ( 0 degrees Celsius to 49 degrees Celsius ).
Does Max Number of B208 Limit the number of B308's that can be used?
Does Max Number of B308s Limit the number of B208 's that can be used?
The maximum number of B208 modules and B308 modules that are available to the panel type can be connected at one time.
The only limit would be available power and SDI2 cable distance specifications which are detailed in the module documentation as well as the panel Installation and System Reference Guide (ISRG).
The D5200 needs to match a Data Lock code in the panel to access programming. Changing the panel Data Lock Code from the default of 12345 will prevent access.
Remote Programming Software:
RPS also needs to match the Data Lock code in the panel to access programming. Changing the panel Data Lock Code from the default of 12345 will prevent access.
RPS also needs to match the RPS Passcode (or RAM Passcode in legacy types) in order to allow access programming. Changing the default from 999999 will block RPS access.