How is the D6112 armed and disarmed?
Arming Your Security System
Your security system can be armed in many different ways, depending on the arming command used. Arming commands are those commands used to arm the system. The most basic arming command is to arm the entire system. This is done by entering your personal passcode and pressing ENT or by entering COMMAND 1.
To ARM your security system:
Enter your personal passcode and press ENT or enter an Arming Command. Your system may be programmed to send a "closing" report to the Central Station when arming.
Disarming Your Security System
Your security system is disarmed by entering your personal passcode and pressing ENT. When your system is armed, you must enter the premises through a designated entry door to prevent an immediate instant alarm condition. Opening the door starts an entry delay time and the Command Center emits a pulsing "beep" tone to remind you to disarm the system. Entering your personal passcode and pressing ENT before the delay time expires and the system will disarm. If you enter through a wrong door or fail to disarm the system before the entry delay expires, you will generate an immediate alarm.
To DISARM your security system:
Enter your personal passcode and press ENT. Your system may be programmed to send an "opening" report to the Central Station when disarming.
How do I Force Arm the System?
Force Arming the System
Under normal conditions your Command Center cannot be master armed while there is a faulted zone. Force arming allows you to arm the system with any zone faulted other than priority zones. (Priority zones are zones that must be normal when the system is armed.) Force arming arms only those zones that are ready to arm; any zone faulted at arming time is bypassed (not armed).
When force arming, a trouble report may be sent to the Central Station indicating that the system was force armed and which zone was faulted. A closing report may also be sent by those systems that are programmed for opening and closing reports.
Force arming can be programmed to apply to most arming commands as well as your personal passcode. Your alarm technician will check the boxes below to indicate which arming commands can force arm your system.
To arm with zones faulted:
1. Enter your personal passcode and press the ENT key, or enter an arming command (COMMANDs 1, 2, or 3). The Command Center then emits a "beep" tone with each keytouch indicating that a zone is faulted. 2. Press the COMMAND bar and then the ENT key. The system now arms all zones which are normal.
NOTE: If the fault is restored (returned to normal) while arming, the zone will be armed. If the fault is restored after arming, how your system is programmed determines whether or not the zone will be armed with the rest of the system.
How do I reset the command center sounder and memory display?
Reset Command Center Sounders*Reset Alarm Memory Display
COMMAND 4 performs two functions for your security system. Use this command to silence your Command Center sounder during service alert, and to reset the Command Center alarm memory.
To use COMMAND 4:
1. Ensure that your security system is disarmed. 2. Press the COMMAND bar. The Command Mode indicator light comes on. 3. Press the 4 key. The Command Center sounder is silenced and any flashing Zone Status indicator lights are turned off if the zone is normal.
What 2 wire smoke detectors have been UL listed compatible with the D4112?
Note : The D4112 is not UL listed for Commercial Fire Applications. This control does not support multiple detectors in alarm. Do not use smoke detectors from different manufacturers on the same circuit.
Head D262 / Base D260 (20 per loop)
Head DS200 / Base MB200-2W (10 per loop)
Head DS200HD / Base MB200-2W (10 per loop)
Head 1400 / Base N/A (10 per loop)
Head 2400 / Base N/A (10 per loop)
Head 2400th / Base N/A (10 per loop)
Head 1451 / Base B401, B401B (10 per loop)
Head 1451DH / Base DH400 (10 per loop)
Head 2451 / Base B401, B401B, DH400 (10 per loop)
Head 2451TH / Base B401, B401B, DH400 (10 per loop)
Head 2300T / Base N/A (10 per loop)
How to work with the D4112 Battery Discharge and Recharge voltage schedule.
When does the D4112 send a Trouble Low Battery report to the monitoring station?
When does the D4112 send the Low Battery restore report to the monitoring station?
When using 4 wire smoke detectors on the D6112, where do the detectors power connections need to be landed on the panel to provide reset capabilities with Command 47?
The power connections need to be landed on terminal 15(+) and 14(-) for the reset to occur when a CMD 47 is entered at the keypad.
How do I do a local system test?
Local System Test
It is easy for you to test your security system without sending reports to the Central Station. This local system test is performed only when the security system is disarmed to ensure that your security system is operating properly, and should be used to test your system regularly.
COMMAND 44 is used to test your security system. This command tests your Command Center, the system’s sounders (both interior and exterior) and the system’s detection devices. No alarm reports are sent to the Central Station unless a 24-hour zone is faulted (e.g.: panic, fire duress). Contact your Central Station before you test your fire protection system because an alarm report may be transmitted.
To test individual detection devices, simply activate sensors and open protected doors and windows one-at-a-time. As detection devices are faulted, the Command Center display panel indicates the faulted zone. This verifies that the detection device is working properly.
To use COMMAND 44:
1. Ensure that the security system is disarmed. 2. Press the COMMAND bar. The Command Mode indicator light comes on. 3. Press the 4 key twice. Audible devices (both interior and exterior) sound. To silence the audible warning, press any numeric key of the Command Center keypad. 4. After silencing the audible devices, you may test detection devices. Open a door or a window, or activate a motion sensor. The Command Center display panel indicates the zone which you have faulted. This verifies that individual devices are working properly. 5. To end the Local System Test simply press any numeric key on the Command Center.
What would cause the D6112 panel to send a zone 9, when arming the system?
D5200 Programing - 7.10 or 8.10 = Comb ID is set to yes in the program of the panel. With this
prompt set to yes in the program, a zone 9 is sent when the panel is armed
by the remote programmer, or command 1.