The B-Series panel onboard relay can be configured for either:
Standard Form-C relay
Aux Power configuration, Right two pins covered, the C terminal has 12Vdc available and upon activation will switch to the NO terminal.
Relay A turned off, NO to Common reads 0Vdc. Relay A turned on, NO to Common reads +12Vdc.
Aux Common configuration, Left two pins covered, the C terminal is Common. Upon activation Common is switched to the NO terminal.
Relay A turned off, NO to Aux= 0Vdc Relay A turned on, NO to Aux= 12Vdc
Dry Contact Configuration No jumper used, NO and C and NC works as a standard dry contact.
Relay A turned off, NO to C= Open, NC to C= Short Relay A turned on, NO to C= Short, NC to C= Open
How do I remove the User Code Tamper on a 6000 series panel?
Follow the below steps per the differant programming options:
> Receive a copy of the panel
> Go into the User Interface
> Go into the Passcode Configuration and Installer Passcode section
> Change User Tamper Retry Count and User Tamper Lockout Time to 0
> Send record back to the panel, disconnect from RPS, and Reset the Panel.
> Lock down the installer pin
> Press CMD 41 and YOUR installer code. (Default is 6543)
> Press 8 to go into Programming Mode
> Type in Nibble 0381 CMD then 0 *
> Then press CMD and you will go to Nibble 0382 and now you will type 0 * again.
> After both of those are set to zero, you will now be able to release the installer pin
What are the steps to default a DS7090 or DS7090i?
To set panel back to factory default perform the following:
Caution - This will erase all programming except for the phone numbers. What may prevent the panel from being set to factory default is a security feature called anti-takeover. If this is enabled the panel will not be able to be set back to factory default
Enter into program mode by the installer code # 0 ( 98765 # 0 ) is the default code, or short the little silver dots next to the last zone on the panel for 4 seconds with a jumper wire.
** Enter 839#, the beeper should sound for steady.
Short the same 2 pins, and the panel should be back to factory default.
** When the step is followed and a 3-beep error tone is generated while after 839# is entered. This panel is lock and will need to be reset at Bosch Security System for a fee. Contact our repair department a 800-289-0096 Ex 4220 M - F 8 a.m. - 5 p.m. EST
After installing RPS Full edition or RPS Lite, the RPS software was then uninstalled and RPS Lite/RPS edition installed; However, the Full/lITE edition of RPS still reinstalled even while using a RPS Lite/RPS Full CD or installation files. Can this be fixed?
The Standby (Reset) pin is not locked down. The panel 12V backup battery is low or missing. Using the wrong product handler, for example, using 2112 instead of 2212. Too much Current Draw on panel. Disconnect devices from Aux Power and try again. Noise or interference on the keypad Data Bus. Disconnect all wires on the panel data terminals. Not enough free memory in the D5200 Programmer. There should be 60K free memory. Refer to KB article: How to Operate the D5200 Hand Held Programmer. The 2212 handler may be corrupted in the D5200. Delete the 2212 handler and re-download it. Refer to KB article: How to Operate the D5200 Hand Held Programmer. Low batteries in the D5200. Replace batteries using 4 C cells. Trying to program a panel that is not powered up The programming cord is not securely connected to the panel programming port or may be damaged. The DX4010V2 comes with a cord with a 4-pin Molex connector on one end and phone connector on other end. This cable may work as a substitute.