The Standby (Reset) pin is not locked down. The panel 12V backup battery is low or missing. Using the wrong product handler, for example, using 2112 instead of 2212. Too much Current Draw on panel. Disconnect devices from Aux Power and try again. Noise or interference on the keypad Data Bus. Disconnect all wires on the panel data terminals. Not enough free memory in the D5200 Programmer. There should be 60K free memory. Refer to KB article: How to Operate the D5200 Hand Held Programmer. The 2212 handler may be corrupted in the D5200. Delete the 2212 handler and re-download it. Refer to KB article: How to Operate the D5200 Hand Held Programmer. Low batteries in the D5200. Replace batteries using 4 C cells. Trying to program a panel that is not powered up The programming cord is not securely connected to the panel programming port or may be damaged. The DX4010V2 comes with a cord with a 4-pin Molex connector on one end and phone connector on other end. This cable may work as a substitute.
When does the D128 dual phone line switcher module indicate a phone line failure?
An amber phone line status LED lights on the D128 module when the control/communicator measures less than 25VDC or 10mA of current across the tip and ring of the telephone line. The D8112 and D9112 monitor the telephone lines for a programmable interval before indicating a trouble condition.
AC Fail/Res Rpt
Parameter Description: AC Power Supervision reports are sent to the central station and local printer at the time programmed for AC Fail Time.
IMPORTANT: To comply with NFPA standards and UL 864 requirements for Commercial Fire Systems, program this item NO and program AC Tag Along as YES.
Yes: Send AC Fail and AC Restoral reports.
No: Do not send AC Fail and AC Restoral reports.
1) Receive copy of 9000MAIN
2) Enter group PANEL WIDE PARAMETER
3) Enter group Power Supervision
4) Fail/Res Rpt Yes/No (SPACE bar to change)
*Must press ENTER for each prompt entry
5) Send Load to panel
Why would the keypad display Not Ready, but no zone number is displayed?
An invisible zone is not ready.
Enter a valid pin number + off to display the zone number of the invisible zone that is not ready.
Part numbers DS7400X, DS7400, DS7400Xi, DS7400XIVER2, DS7400XIVER3+, DS7400XIVER4+, DS7447
The D5200 needs to match a Data Lock code in the panel to access programming. Changing the panel Data Lock Code from the default of 12345 will prevent access.
Remote Programming Software:
RPS also needs to match the Data Lock code in the panel to access programming. Changing the panel Data Lock Code from the default of 12345 will prevent access.
RPS also needs to match the RPS Passcode (or RAM Passcode in legacy types) in order to allow access programming. Changing the default from 999999 will block RPS access.
When a resistor is on one of the expansion points, it shows "shorted" in the view point status. When the resistor is removed, it shows "open" in the view point status. What should be done?
Watch Mode Only- This point will not create alarm or trouble responses and will not generate reports to the Central Monitoring Station.
Program the Point: Select Point Type= 0. Select all Yes/No options= NO. Set Alarm Report Routing = 0: No Reports, No Events to Log/Printer. Set Restoral Report Routing = 0: No Reports, No Events to Log/Printer. Select Watch Tone and enable Watch Point: Select [Cmd] + 62 to select the watch tone. Select [Cmd] + 63 to select the watch point(s).
When the panel auto arms, will it bypass all points faulted even if it surpasses the bypass max? D9412,D9412G,D7412G,D7212G,D7412,D4412,D6412,D7212,D7212B,D7212B1,D9412GV2,D7412GV2,D7212GV2,D9412GV3,D7412GV2,D7212GV2,D9412GV3,D7412GV3,D7212GV3,D9412GV4,D7412GV4,D7212GV4,